Submerged Servers: Green Revolution Cooling
Are data center operators ready to abandon hot and cold aisles and submerge their servers? Startup Green Revolution Cooling has developed a liquid cooling enclosure that it says can cool high-density server installation for a fraction of the cost of air cooling in traditional data centers.
The Austin-based company’s CarnotJet Dielectric Fluid Submersion Cooling System resembles a rack tipped over on its back, with servers inserted vertically into slots in the enclosure, which is filled with a coolant similar to mineral oil.
Green Revolution says its approach can produce large savings on infrastructure, allowing users to operate servers without a raised floor, CRAC units or chillers. The company launched at SC09 conference last fall, and is targeting will soon install its first units at the Texas Advanced Computing Center, home to the Ranger supercomputer
In this video from Data Center World, Green Revolution co-founder Christiaan Best provides an overview of his company’s offering, along with a look at a demo of a “swimming server” at the company’s booth.
As Best indicates in the video, submersion cooling isn’t new. Mineral oil has been used in immersion cooling because it is not hazardous, transfers heat almost as well as water but doesn’t conduct an electric charge. Many readers may be familiar with Fluorinert, a dielectric coolant from 3M that was used in the Cray 2 and other supercomputers. An immersion system with a different design was introduced by UK firm Iceotope at the SC09 event.
Green Revolution says its GreenDEF coolant has been “optimized for data centers” and can support heat loads of up to 100 kilowatts per 42U rack, far beyond current average heat loads of 4 to 8 watts a rack and high-density loads of 12 to 30 kilowatts per rack. The company says the CarnotJet system is designed to comply with fire codes and the Clean Water Act, and integrates with standard power distribution units (PDUs) and network switches.
Some mineral oil-style coolants can be messy to maintain. The company says the coolant can be drained for enclosure-level maintenance, and individual servers can be removed for work, a process documented by Green Revolution in this video:
[...] Submerged Servers: Green Revolution Cooling « Data Center Knowledge [...]
[...] Data Center Knowledge [...]
[...] Via: Data Center Knowledge [...]
[...] up is the story about the new submerged server liquid cooling system. I’m not going to comment on the liquid cooling idea, but I was interested to see the claim [...]
[...] ready to abandon hot and cold aisles and submerge their servers? An Austin startup says its liquid cooling enclosure can cool high-density server installations for a fraction of the cost of air cooling in traditional [...]
delldcexpdPosted March 19th, 2010
Interesting indeed. although, this does raise many questions. just to name a few:
Why did they remove the cdrom?
How are they going to implement this solution? Someone has to apply the new thermal grease under the cpu and who coats/seals the hdds?
How will this process be streamlined for large implementations?
Will it be possible to stack multiple server racks for high density datacenters?
ZerassarPosted April 5th, 2010
While most of your questions are very valid (delldcexpd).
Your one on CDROM removal seems to have quite an obvious answer.
They are submerging the entire server in a high viscosity oil.
The CD could not spin correctly and the laser would be near useless in this liquid.
Easily enough to get by with USB CD/DVD drives though. Not as though you need one permanently plugged in.
“far beyond current average heat loads of 4 to 8 watts a rack” …. uhh, that would be nice