A fire at a major carrier hotel in Toronto left several data center customers offline for hours over the weekend. Peer 1 Networks reported that a fire broke out at 2:26 a.m. Sunday (Eastern time) in an eighth-floor electrical room at 151 Front Street 
, the city’s primary telecom hub. The fire broke out in a section of Peer 1 Networks’ colocation facility housing UPS equipment, causing power to be shut off to the seventh and eight floors, and prompting a vigorous response from Toronto emergency services, which dispatched at least 17 fire units 
to the building.
“There was a fire which was localized to the 802 Suite UPS room within the 151 Front Street Facility,” Peer 1 reported on its forum 
. “The Fire Department mitigated the fire with dry chemical and CO2 extinguishers. No water was used, and all PEER 1 equipment (with the exception of the UPS), and ALL client equipment is unharmed.” Peer 1 said it was able to bypass the UPS system – which typically is positioned between the utility feed and the data center – and restore power to the affected areas by 5 a.m. Eastern time Sunday morning.
The first broke out two days after a more serious electrical fire at Seattle telecom hub Fisher Plaza 
that left many web sites hosted at the building down for more than a day.
Article printed from Data Center Knowledge: http://www.datacenterknowledge.com
URL to article: http://www.datacenterknowledge.com/archives/2009/07/06/fire-causes-outage-at-toronto-carrier-hotel/
URLs in this post:
 151 Front Street: http://www.151frontstreet.com/
 17 fire units: http://ninjamonkey.us/wordpress/wp-content/uploads/2009/07/151frontfire.png
 forum: http://forums.peer1.com/viewtopic.php?f=37&t=117
 Fisher Plaza : http://www.datacenterknowledge.com/archives/2009/07/03/major-outage-at-seattle-data-center/
 Rich Miller: http://www.datacenterknowledge.com/archives/author/richm/
Click here to print.